Corning, CA Air Conditioning & Heating Services from Climate and Energy Solutions
From scheduling the service call or equipment installation, to the completion of the repair or new system install you are handled with honest, professional, affordable care. We are locally-owned, family-operated business that is a part of this community.
Check out what some of our customers are saying about Climate & Energy Solutions services.
for Corning, CA
Rachel - Corning, CA 96021
Overall great service and very polite and professional.
Terry - Corning, CA 96021
Jeremy is very knowledgeable and competent. Pleasant to deal with
Timely service and repair
Henry - Corning, CA 96021
Sonnie - Corning, CA 96021
on time, very professional, knowledgeable
Repairing a Mitsubishi mini split in Corning
Furnace repair on a Ruud gas furnace in Corning.
Installed 5 ton six head Mitsubishi mini split and two branch boxes
Performed HVAC Escrow Inspection, noted down findings and put in form. System still cooling and operational. Tech Findings: Found very low dual run capacitor for the outdoor condenser. AC is having a hard time starting up due to the low capacitor, and it could cause a cooling failure at the compressor and/or the outdoor fan motor in future, recommend replacing. Also found a low indoor blower capacitor for the air handler, which also could lead to the motor eventually going out as well. Recommend replacing both capacitors.
Maintenance on a day & night air conditioner in Corning
Customer having issue of furnace not firing up after draft motor comes on. Tested system and diagnosed there were pressure switch issues. Cleaned out the pressure switch tube and replaced pressure switch. Tested system multiple times, it is now heating and operational at this time. Customer will let us know if future problems arise. Serviced customer on South St in Corning, CA.
Performed full heating maintenance on rooftop package gas unit. Checked amperages of indoor blower motor and inducer draft motor. Checked capacitor for inducer motor. Verified proper voltage and fuse conditions. Cleaned pressure switch tube and cleaned flame sensor. Ran tested heating on both zones. Checked airflow and temperature split as well as thermostat functionality. Checked both air filters. System heating and operational at this time. Serviced customer on Florence Ave in Corning, CA
Heater repair in Orland
Found and repaired refrigerant leaking on suction line. Wires were rubbing on copper causing it to cut though and make a hole. Pressure tested system, vacuumed down system, then recharged with 4.5lbs of refrigerant. Checked system operations and temperature split. Everything checked out, system now cooling and operational at this time. Serviced unit in Corning CA
Fixing an AC system!
Fixing an AC system!
Performed cooling maintenance on two condenser units, checked amperages on compressor and motor washed outdoor coil and changed indoor filters. Fixed buzzing issue with unit number two tested a few times to ensure buzzing was gone. Checked temperature split between both units. System operational and cooling at this time. Serviced unit on Blackburn Ave in Corning, CA